Second, softened water design selection guide
1, softened water equipment selection
The selection of softened water equipment is mainly based on water demand, raw water hardness and applicable occasions
(1) the same amount of water equipment, there are a variety of models, according to the actual water situation selected.
(2) raw water hardness: dark blue boiler softened water equipment, dark blue fully softened water equipment, softened water treatment equipment
When the hardness of raw water ≤ 3m · mol / L, you can choose the time control type, according to the maximum water production equipment;
When the hardness of raw water ≤ 6m · mol / L, it can be selected according to the maximum water capacity of the equipment in the table.
When the hardness of raw water is less than 8m · mol / L, the average value of water production capacity can be selected.
Raw water hardness of 8 ~ 10m · mol / L, according to the minimum water production capacity of equipment, or the use of multi-level system;
Raw water hardness ≥ 10m · mol / L, to be selected multi-level treatment, the general two-level treatment can meet the requirements.
(3) water use: If the Bae Yong hot water boiler or other similar equipment, according to the equipment of the highest water production capacity selection; if the steam boiler water supply, generally according to the boiler evaporation 1.2 times the equipment and water production capacity to match.
Hangzhou Shuidun Technology is specialized in the production and development of stainless steel water treatment products with high quality and resonsable price, it is the preferred product of reverse osmosis water treatment works. Welcome for an inquiry.