Make a detailed record.
3, inspection cycle: water treatment equipment daily continuous production period, the daily production should be routine inspection, do check records; in the non-continuous production period, before each production or weekly routine check and do Good record
Fourth, the water treatment equipment maintenance and equipment troubleshooting:
(1) filter filter should be replaced frequently, depending on the raw water to determine the replacement frequency.
(2) reverse osmosis membrane if the previous treatment is reasonable, into the RO membrane water quality meet the requirements, and according to the operation method of equipment and timely maintenance, the membrane life of up to 2 years. But with the scale, bacteria and other pollutants in the formation of water and water quality will gradually decrease.
a. If the yield is reduced by 15% due to temperature and pressure factors, the reverse osmosis equipment needs to be chemically cleaned.
b. Water quality gradually decreased, more than the relevant standards (excluding factors of raw water changes), then the reverse osmosis equipment requires chemical cleaning.
c. Chemical cleaning must be carried out by professional personnel. Please refer to the Appendix "Troubleshooting and Chemical Cleaning List" for technical questions.
(3) equipment installation site temperature should be between 4 ℃ ~ 45 ℃, long-term equipment, should be added in the system preservatives, the first addition of preservatives should be carried out under the guidance of professionals.
Hangzhou Shuidun Technology is specialized in the production and development of stainless steel water treatment products with high quality and resonsable price, it is the preferred product of reverse osmosis water treatment works. Welcome for an inquiry.